Post questions, comments, reviews or page errors in the comment box below.
Your File is Ready … Download PDF
PDF Content Summary: 25 Interchange way, Vaughan Ontario. L4K 5W3 Phone: 905.660.4655; Fax: 905.660.4113 INSTALLATION AND MAINTENANCE INSTRUCTIONS Web: mircom.com MIX-4040 DUAL INPUT MODULE
ABOUT THIS MANUAL This manual is included as a quick reference for installation. For fur ther information on the use of this device with a FACP, please refer to the panel’s manual. Note: This manual should be left with the owner/operator of this equipment. MODULE DESCRIPTION The MIX-4040 Dual Input module is designed to operate with a listed compatible intelligent fire system control panel. The module can sup port one Class A or 2 Class B inputs. When configured for Class A operation, the module provides an internal EOL resistor. When con figured for Class B operation, the module can monitor two indepen dent input circuits while using only one module address. The address of each module is set using the MIX-4090 programmer tool and up to 240 units may be installed on a single loop. The module has a panel controlled LED indicator. FIGURE 1 MODULE FRONT: LED PROGRAMMER INTERFACE SPECIFICATIONS Normal Operating Voltage: 15 to 30VDC Alarm Current: 3.3mA Standby Current: 2mA with two 22k EOL EOL Resistance: 22k Ohms Maximum Input Wiring Resistance: 150 Ohms total Temperature Range: 32F to 120F (0c to 49C) Humidity: 10% to 93% Non-condensing Dimensions: 4 5/8”H x 4 1/4” W x 1 1/8” D Mounting: 4” square by 2 1/8” deep box Accessories: MIX-4090 Programmer BB-400 Electrical Box MP-302 EOL on mounting plate Wiring range on all terminals: 22 to 12 AWG MOUNTING Notice: You must disconnect power from the system before installing the module. If this unit is being installed in a system that is currently operational, it is necessary to inform the operator and the local authority that the system will be temporarily out of service. The MIX-4040 module is intended to be mounted in a standard 4” square back-box (see Figure 2). The box must have a minimium depth of 2 1/8 inches. Surface mounted electrical boxes (BB-400) are available from Mircom. FIGURE 2 MODULE MOUNTING: WIRING: Note: This device should be installed as per applicable requirements of the authorities having jurisdiction. This device shall be connected to power limited circuits only. 1. Install the module wiring as indicated by the job drawings and appropriate wiring diagrams (see Figure 3 for an example of wring for a Class A connected device and Figure 4 for an example of Class B) 2. Use the programmer tool to set the address on the module as indicated on the job drawings. 3. Mount the module in the electrical box as shown in figure 2.
LT‐6139 rev 1.2 7/18/19
FIGURE 3 SAMPLE CLASS A WIRING: TO PANEL OR NEXT DEVICE SLCRXWï SLCout+ SLCLQï SLCin+ FROM PANEL OR PREVIOUS DEVICE FIGURE 4 SAMPLE CLASS B WIRING: TO PANEL OR NEXT DEVICE SLC SLC+ SLC SLC+ A A B B − + − + IN$ï INA+ IN%ï INB+ E.O.L RESISTOR INSDE THE MODULE
SLCRXWï SLCout+ SLC SLC+ A A B MP-302 (22k) IN$ï − INA+ + IN%ï −
FROM PANEL OR PREVIOUS DEVICE SLCLQï SLCin+ SLC SLC+ B + INB+ MP-302 (22k)
LT‐6139 rev 1.2 7/18/19
FREE ENGLISH PDF
USER GUIDE - USER MANUAL
OWNER GUIDE - OWNER MANUAL
REFERENCE GUIDE - REFERENCE MANUAL
INSTRUCTION GUIDE - INSTRUCTION MANUAL