Post questions, comments, reviews or errors in the comment box below.
Your File is Ready … Download PDF
PDF Content Summary: INSTALLATION INSTRUCTIONS SAVE THESE INSTRUCTIONS LPW2045C 208 Volt and LPW2445C 240 Volt MODELS Power must be brought to the heater first - then to wall thermostat Instructions for ceiling mount unit with remote wall thermostat It is extremely important to verify that the electrical power supply is the same voltage as the heater you are installing. 208 / 240 / 277 and 120 Volt heaters are not interchangeable! Powering a 208 / 240 / 277 Volt unit with 120 Volt supply wires will reduce the heater's output by approximately 75%. Powering a 120 Volt unit with 208 / 240 / 277 Volt supply wires will destroy the heater and voids all warranties. NOTICE: The power must be brought to the heater first (not to the wall mounted or remote thermostat). This is necessary to provide power for the fan to cool down the element after the thermostat has opened. Use a single pole line voltage wall thermostat or switch to control this heater. CAUTION: Open the circuit breaker supplying the heater before attempting installation, maintenance, or repairs. Lock or tag circuit breaker panel door. Failure to do so could result in serious electrical shock, burns, or possible death. 1. Remove heater contents from carton. 2. Remove grille by loosening the four mounting screws along the sides of the front panel. 3. Detach interior assembly from the ceiling case by removing the four screws along each side of the interior panel. Lift and tilt assembly away from the top of the ceiling case. Free the bottom edge from the metal lip inside the ceiling case. Place the interior assembly in a safe location until the ceiling case is mounted. 4. Mount heater enclosure can on ceiling joists a minimum of 6" from side wall, using the holes provided in the sides of the case. The face of the case should be flush with the finished ceiling surface. Installation of the interior and grille to the ceiling case will cover an approximate 1/2" periphery along the outer area of the opening. 5. Mount heater wall installation case on wall studs a minimum of 6" from side wall or open edge of a door and a minimum of 4" from floor (10" recom- mended), using the holes provided in the sides of the case. The face of the case should be flush with the finished wall. Installation of the interior and grille to the ceiling case covers an approximate 5/8" periphery along the outer area of the opening. 6. After ceiling case is secured, interior assembly leads may be attached to supply wires and interior secured to ceiling case. NOTE: The LPW heater is equipped with two steel elements having a capacity of 2250 Watts each, for a combined capacity of 4500 Watts. The heater is factory-wired at 4500 Watts. To adjust the heater for lower wattages remove the appropriate colored wire according to the illustration and wattage diagram provided on the back side of this sheet. Be sure to insulate and secure the unused lead. 7. Reinstall interior assembly on ceiling case using screws provided. 8. Mount grille to interior with screws provided. 9. Installation is now complete and the heater ready for use. 10. Use a single pole line voltage wall thermostat or switch only to control this heater. Maintenance & Warranty The high quality and superior design of this unit will enable years of maintenance-free performance. Once yearly the heater should be checked for lint or dust accumulation but no further maintenance is required. The motor is permanently lubricated and sealed. A five year warranty is provided on the Pic-A-Watt element and 1 year on all materials, components and workmanship. OWNERS GUIDE & INSTALLATION INSTRUCTIONS SHOULD BE LEFT WITH HEATER FOR HOME OWNER KING ELECTRICAL MFG. COMPANY • 9131-10th Ave South • Seattle, WA 98108 • Phone (206) 762-0400 • Fax (206) 763-7738 • king-electric.com INSTALLATION INSTRUCTIONS SAFETY LIGHT SAVE THESE INSTRUCTIONS NOTICE - The light may illumi- nate periodically during normal operation for 10 to 45 seconds. This flashing is not a hazard. If the light stays on steadily for 1 to 5 minutes an over-temperature condition probably exists and the heater should be examined. INSTALLATION INSTRUCTIONS This heater is shipped from the factory wired for maximum wattage of 4500 Watts. To reduce the wattage unplug (disconnect) an insulated push on terminal and wrap with electrical tape to prevent the possibility of electrical contact with other parts. WIRE COLOR CODING A - Orange - disconnects the 1000 Watt element B - Blue - disconnects the 750 Watt element C - Yellow - disconnects the 500 Watt element D - Black - Energized Common Leg Do Not Disconnect E - Red - Do Not Disconnect D Common A BC 1000750 END VIEW OF ELEMENT SHOWING QUICK CONNECT TERMINALS A - 1000 WATT B - 750 WATT C - 500 WATT D - COMMON LEG OF POWER SUPPLY 2250 - 2750 - 3000 - 3250 - 3750 - 4000 - 4500 WATTAGES AVAILABLE IN ONE UNIT OWNERS GUIDE & INSTALLATION INSTRUCTIONS SHOULD BE LEFT WITH HEATER FOR HOME OWNER KING ELECTRICAL MFG. COMPANY • 9131-10th Ave South • Seattle, WA 98108 • Phone (206) 762-0400 • Fax (206) 763-7738 • king-electric.com 213⁄4" 13" Safety Light 1⁄2" RED E1000 WATT This heater includes a visual alarm to warn that parts of the heater are getting excessively hot. If the alarm flashes, BLUE B750 WATT immediately turn the heater off and inspect for any objects on or adjacent to the heater YELLOW C500 WATT that may cause high temperatures. Insulated Terminal Push on ORANGE A1000 WATT RED E750 WATT RED E Insulated Terminal Push on ORANGE Wall Thermostat Leads LINE LPW2045C LPW2445C LPW 2045C-2445C.indd : 9/09 500 WATT 1 3 2 1D Pic-A-Watt® Metal Sheath Element FAN DELAY 500 LIMIT MOTOR K CALBLINE 2 HAZARD LIGHT BLACK BLACK
FREE ENGLISH PDF
USER GUIDE - USER MANUAL
OWNER GUIDE - OWNER MANUAL
REFERENCE GUIDE - REFERENCE MANUAL
INSTRUCTION GUIDE - INSTRUCTION MANUAL