Post questions, comments, reviews or errors in the comment box below.
Your File is Ready … Download PDF
PDF Content Summary: ZP700 Installation Series Sheet Addressable Detector 1 2 3 4 EN: Installation Sheet Description ZP700 Series Addressable Detector models are shown in Table 1. Table 1: Models Number Description ZP720-3P Addressable Thermal Sensor, Polar White ZP730-2P ZP730-2B ZP730-2S30 Figures Figure 1: Inserting the detector Figure 2: Position of the locking tab Figure 3: Removing a locked detector Figure 4: Setting the address Installation Addressable Optical Smoke Sensor, Polar White Addressable Optical Smoke Sensor, Black Addressable Optical Smoke Sensor, Chubb Note: For general guidelines on system planning, design, installation, commissioning, use and maintenance, refer to the EN 54-14 standard and local regulations. ZP732-2P ZP732-2S30 To install a detector: Insert the detector head into the mounting base and rotate it clockwise until it clicks into place (Figure 1). The detector may be locked into the mounting base if required. To do this, remove the locking tab before installation shown in Figure 2. Combination Smoke and Heat Detector, Polar White Combination Smoke and Heat Detector, Chubb © 2014 UTC Fire & Security. All rights reserved. 1 / 4 P/N 501-1244ZE-1-05 • REV 05 • ISS 05MAR14 Specifications ZP730-2P/2B ZP730-2S30 After installation, ensure that the detector communicates with the control panel. Always test detectors after installation. To remove a locked detector: 1. Insert a small screwdriver into the locking tab slot (Figure 3). 2. Press and rotate the detector anticlockwise. Setting the address The detectors include a seven-segment DIP switch (SW1) for assigning device addresses. Each switch segment has a decimal value as shown in Figure 4. The address is the sum of all the switch segments in the ON position. The full DIP switch address range of 1 to 127 is shown on page 4. For example, to select a device address of 007, set SW1-1, SW1-2, and SW1-3 to the ON position and the remaining switch segments to the OFF position. Locking base option The sensors are compatible with a range of bases (see “Specifications”) and are easily installed by a simple twist and lock action. Note: To prevent unauthorised removal of a device from its base, an automatic locking tab is incorporated into all sensor mouldings. If the tab is removed, sensors can only be released from their bases by use of a screwdriver, as shown in Figure 3. This locking option is applied at the system commissioning stage. Maintenance and testing Basic maintenance consists of a yearly inspection. Do not modify internal wiring or circuitry. Automatic self-test Sensor sensitivity, calibration and self-testing are carried out automatically by the fire panel. Removal or replacement of an incorrect sensing device will be identified by the system and shown as a fault. ZP720-3P ZP732-2P ZP732-2S30 Operating voltage 19.5 to 20.5 VDC 19.5 to 20.5 VDC Current Standby Alarm 600 μA 700 μA 600 μA 700 μA Coverage ZP730-2P/2B: 100 m2 ZP730-2S30: 100 m2 ZP720-3P: 50 m2 ZP732-2P: 100 m2 smoke element/ 50 m2 thermal element ZP732-2S30: 100 m2 smoke element/ 50 m2 thermal element IP Rating IP32 IP32 Polarity sensitive Yes Yes Compatible bases ZP7-IB-P ZP7-SB1-B ZP7-SB1-P ZP7-RB1-P ZP755B-2P ZP755BV-3 ZP755BV-4P ZP755BV-5P ZP7-IB-P ZP7-SB1-B ZP7-SB1-P ZP7-RB1-P ZP755B-2P ZP755BV-3 ZP755BV-4P ZP755BV-5P Compatible accessories Z-RL4 Remote LED unit Z-RL4 Remote LED unit Operating temperature Storage temperature Relative humidity –10 to +75°C –20 to +70°C 20 to 95% noncondensing –10 to +85°C –20 to +70°C 20 to 95% noncondensing Dimensions (Ø x H) 106 × 52 mm ZP720-3P: 106 × 52 mm ZP732-2P: 106 × 58 mm ZP732-2S30: 106 × 58 mm Weight 105 g ZP720-3P: 85 g ZP732-2P: 105 g ZP732-2S30: 105 g Regulatory information This section includes both regulatory information and a summary on the declared performance according to the Construction Products Regulation 305/2011. For detailed information refer to the product Declaration of Performance. Certification Certification body 0370 Declaration of Performance number ZP720-3P ZP730-2P/2B/2S30 ZP732-2P/2S30 360-4211-0399 360-4211-0199 360-4211-0299 Year of first CE marking 05 Product Identification ZP720-3P ZP730-2P ZP730-2B ZP730-2S30 ZP732-2P ZP732-2S30 2 / 4 P/N 501-1244ZE-1-05 • REV 05 • ISS 05MAR14 Intended use See DoP point 3 Essential characteristics See DoP point 9 Manufacturer Gulf Security Technology Co.,Ltd 80, Changjiang East Road, QETDZ, Qinhuangdao, Hebei Province, China 066004 Authorized EU manufacturing representative: UTC Fire & Security B.V. Kelvinstraat 7, 6003 DH Weert, Netherlands European Union directives 1999/5/EC (R&TTE directive): Hereby, UTC Fire & Security declares that this device is in compliance with the essential requirements and other relevant provisions of Directive 1999/5/EC. 2002/96/EC (WEEE directive): Products marked with this symbol cannot be disposed of as unsorted municipal waste in the European Union. For proper recycling, return this product to your local supplier upon the purchase of equivalent new equipment, or dispose of it at designated collection points. For more information see: recyclethis.info. Contact information For contact information, see utcfssecurityproducts.eu. P/N 501-1244ZE-1-05 • REV 05 • ISS 05MAR14 3 / 4 4 / 4 P/N 501-1244ZE-1-05 • REV 05 • ISS 05MAR14
FREE ENGLISH PDF
USER GUIDE - USER MANUAL
OWNER GUIDE - OWNER MANUAL
REFERENCE GUIDE - REFERENCE MANUAL
INSTRUCTION GUIDE - INSTRUCTION MANUAL