Post questions, comments, reviews or errors in the comment box below.
Your File is Ready … Download PDF
PDF Content Summary: NO. OOO2076521 (0) No. 2080147(11) 1/18 Model 8169 Page 1 of 4 INSTALLATION, OPERATION & MAINTENANCE INSTRUCTIONS 1455 Kleppe Lane ◆Sparks, NV 89431-6467 ◆(775) 359-4712 ◆Fax (775) 359-7424 E-mail: firstname.lastname@example.org ◆ website: hawsco.com Model 8169 Shower NOTE TO INSTALLER: Please leave this information with the Maintenance Department. LIMITED WARRANTY HAWS® warrants that all of its products are guaranteed against defective material or poor workmanship for a period of one year from date of shipment. HAWS liability under this warranty shall be discharged by furnishing without charge F.O.B. HAWS Factory any goods, or part thereof, which shall appear to the Company upon inspection to be of defective material or not of first class workmanship, provided that claim is made in writing to company within a reasonable period after receipt of the product. Where claims for defects are made, the defective part or parts shall be delivered to the Company, prepaid, for inspection. HAWS will not be liable for the cost of repairs, alterations or replacements, or for any expense connected therewith made by the owner or his agents, except upon written authority from HAWS, Sparks, Nevada. HAWS will not be liable for any damages caused by defective materials or poor workmanship, except for replacements, as provided above. Buyer agrees that Haws has made no other warranties either expressed or implied in addition to those above stated, except that of title with respect to any of the products or equipment sold hereunder and that HAWS shall not be liable for general, special, or consequential damages claimed to arise under the contract of sale. The emergency equipment manufactured by HAWS is warranted to function if installation and maintenance instructions provided are adhered to. The units also must be used for the purpose, which they were intended. This product is intended to supplement first-aid treatment. Due to widely varying conditions HAWS cannot guarantee that the use of this emergency equipment will prevent serious injury or the aggravation of existing or prior injuries. NO OTHER WARRANTIES EXPRESSED OR IMPLIED ARE AUTHORIZED, PROVIDED OR GIVEN BY HAWS. SHOULD YOU EXPERIENCE DIFFICULTY WITH THE INSTALLATION OF THIS MODEL PLEASE CALL: TECHNICAL SUPPORT: 1-800-766-5612 FOR CUSTOMER SERVICE: 1-888-640-4297 LOCATION OF UNIT: The Model 8169 Emergency Shower should be installed in close proximity to potential accident areas. It should be clearly identified free from obstructions and easy to access. SUPPLY LINE: The minimum recommended line size is 1” IPS with 30-90 psi (2-6 ATM) flowing pressure. Where sediment or mineral content is a problem, an inlet filter is recommended. PLUMBING CONNECTIONS: Inlet supply is female 1” IPS. TROUBLESHOOTING PROBLEM REPAIR CHECKLIST 1. No flow. 1. Check the main shut-off valve. 2. Insufficient water flow at the showerhead. 2. a. Verify minimum 30 psi (2 ATM) flowing supply line pressure. b. Probable clogging of flow control inside showerhead. Unscrew showerhead off of 1” x 5” nipple and clean rubber flow control. For more information about Haws products, see our website: hawsco.com © 2018 Haws® Corporation – All Rights Reserved HAWS® and other trademarks used in these materials are the exclusive property of Haws Corporation. 1/18 Model 8169 Page 2 of 4 ITEM THIS DOCUMENT IS TRUE AND CORRECT AT TIME OF PUBLICATION. CONTINUED PRODUCT IMPROVEMENTS MAKE SPECIFICATIONS AND MEASUREMENTS SUBJECT TO CHANGE WITHOUT NOTICE. DESCRIPTION WHEN ORDERING PARTS PLEASE SPECIFY MODEL NUMBER. PART NO. 1455 KLEPPE LANE PARTS BREAKDOWN SPARKS, NEVADA 89431 (775) 359-4712 FAX (775) 359-7424 E-MAIL: HAWS@HAWSCO.COM WEBSITE: HAWSCO.COM ECN NO. REVISED PER BY MODEL(S) CHKD CLF 3/9/93 APPROVED 11 Haws Corporation - All Rights Reserved PAGE HAWS and other trademarks used in these materials are the exclusive property of Haws Corporation. PART NUMBER ECN: 5279 VWC DRAWN DATE8169 0002080147 DATE VWC SHOWER REVISION FV 02/16/18 SCALE: NA DRAWING TYPE: PARTS BREAKDOWN SIZE: A SHEET 1 OF 1 C 2018 3 OF 4 R THIS DOCUMENT IS TRUE AND CORRECT AT TIME OF PUBLICATION. CONTINUED PRODUCT IMPROVEMENTS MAKE SPECIFICATIONS AND MEASUREMENTS SUBJECT TO CHANGE WITHOUT NOTICE. 21 3/8" HANGER BRACKET (543mm) (NOT SUPPLIED) 1" IPS SUPPLY (NOT SUPPLIED) 3" X 1/2" 6" (152mm) (244mm) 9 5/8" (41mm) FLANGE DIA FLOOR LINE TRF 5/25/91 11 4 F O4 SLOT (Ø254mm) INSTALLATION E GAPDATE: DATE: (76mm X 13mm) 1 5/8" SUSPENDED (267mm) 10 1/2" CEILING 8 5/8" (219mm) ESCUTCHEON (SUPPLIED) 82" MIN - 96" (2083mm MIN - 2438mm) 51 1/2" MIN - 65 1/2" (1308mm MIN - 1664mm) APPROVED: Ø10" NOTES: CEILING CUTOUT 1. WHEN INSTALLING THIS UNIT, LOCAL , STATE, OR FEDERAL CODES SHOULD BE ADHERED TO FOR INSTALLATION DIMENSIONS (LOCATIONS), WASTE AND SUPPLY REQUIREMENTS OTHER THAN SHOWN. 2. TO COMPLY WITH ANSI Z358.1-2014 FOR EMERGENCY SHOWER EQUIPMENT: - SHOWER SHALL BE POSITIONED SUCH THAT SHOWER HEAD IS NO LESS THAN 82" (2083mm) AND NO GREATER THAN 96" (2438mm) FROM SURFACE ON WHICH USER STANDS. - SHOWER SPRAY PATTERN SHALL HAVE A MINIMUM DIAMETER OF 20" (508mm) AT 60" (1524mm) ABOVE SURFACE ON WHICH USER STANDS, AND CENTER OF SPRAY PATTERN SHALL BE LOCATED NO LESS THAN 16" (406mm) FROM NEAREST OBSTRUCTION. 3. DIMENSIONS MAY VARY BY ±1/2" (13 mm). 1455 KLEPPE LANE SPARKS, NEVADA 89431 (775) 359-4712 FAX (775) 359-7424 E-MAIL: HAWS@HAWSCO.COM WEBSITE: HAWSCO.COM ECN NO. REVISED PER BY: MODEL(S) CHK'D.: C Haws Corporation - All Rights Reserved. HAWS R and other trademarks used in these materials are the exclusive property of Haws Corporation. PART NUMBER 5279 VWC 8169 0002080147.D VWC SHOWER FV 02/16/18 SCALE: NA SHEET 1 OF 1 2018 ECN: DRAWN: REVISION DRAWING TYPE: SIZE: A
FREE ENGLISH PDF
USER GUIDE - USER MANUAL
OWNER GUIDE - OWNER MANUAL
REFERENCE GUIDE - REFERENCE MANUAL
INSTRUCTION GUIDE - INSTRUCTION MANUAL