Post questions, comments, reviews or page errors in the comment box below.
PDF Content Summary:
****** Page 1 ****** INSTALLING THE SMOKE ALARM This smoke alarm is powered by a battery and requires no additional wiring. Having established the mounting location ensure that there in no electrical wiring or pipe work in the area adjacent to the mounting surface. Take the mounting bracket and mark the two mounting hole locations. Drill holes in the positions marked. Insert wall plugs into the drilled holes. Screw mounting bracket to mounting surface. DO NOT OVER TIGHTEN. Insert a 9V battery firmly into battery com- partment on the rear of the detector. NOTE POLARITY OF CONNECTIONS. Ensure the metal tab is fully depressed when the battery has been fitted. NOTE— For the safety of the end user the smoke alarm cannot be fitted without its battery Assemble detector onto the mounting plate by aligning the two projections on the mounting plate with the two keyhole slots in the detector. Lock in position by giving a clockwise quarter turn. Test the correct operation of the smoke detector by depressing the test button on the front of the detector. The unit should emit a loud pulsating alarm. OPERATING YOUR SMOKE ALARM Once the smoke alarm has been installed a small indicator light (LED), positioned under the test button, should flash approxi- mately once a minute in normal operation. If smoke is detected the unit will emit a load pulsating alarm until the air is clear. TESTING YOUR SMOKE ALARM It is recommended that you test your smoke alarm once a week to ensure the detector is working correctly. Push and hold the test button for approxi- mately 3 seconds. A loud pulsating alarm should sound to indicate the correct functiom During the alarm condition the indicator light will flash quickly. PHOTO-ELECTRIC SMOKE ALARM instruction manual MODEL CC-5RS Built-in Hush or Silence feature 3 o 3 WHERE TO PLACE SMOKE ALARMS o o SPECIFICATION: Certificate: Measure: Horn Level: Ambient Humidity: Weight: Operation Temperature: Approved to: Power Source: owysr. O ground floor Fire extinguisher w.t. VdS/EN 14604 85 db(A) 3m 120 g + 40 – + 500 VdS standard 1 x 9V-blockbattery (brand quality) EN 14604 basement o top floor O O Photo-electric srnoke alarm Minimum Best possible protection Main way Beside way G207142 ENi4604 2005 Vertriebsgesel schaft mbH GERMANY – HAMBURG
****** Page 2 ****** This instruction leaflet contains important information on the correct installation and operation of your smoke alarm. Read this leaflet fully before attempting installation and retain for future reference. LOCATING THE SMOKE ALARM This smoke alarm is a single station photoelectric alarm and should NOT be connected to other smoke alarms. If your dwelling is on a single storey, for minimum protection you should fit an alarm in the hallway between the living areas (incl- Kitchens) and sleeping areas. Place it as near to the living areas as possible and ensure the alarm is audible when the bedrooms are occupied. If your dwelling is multi-storey, for mini- mum protection one alarm should be fitted at the bottom of the staircase with further alarms fitted on each upstairs landing. This includes basements but excludes crawl spaces and unfinished attics. NOTE: For maximum protection an alarm should be fitted in every room (except kitchen, bathroom and garage). DO NOT FIT AN ALARM IN THE KITCHEN or BATHROOM, as cooking fumes or steam may trigger the alarm. DO NOT FIT ALARM IN A GARAGE, as exhaust fumes are likely to set it off. POSITIONING THE SMOKE ALARM Ceiling Mounting As hot smoke rises and spread out, it is advisable to mount on a ceiling in a central position. Avoid areas where there is no air circulation. E.g. Corners of rooms and keep away from items which may prevent the free flow of air. Place the unit at least 300 mm from and light fitting or decorative object which might obstruct smoke / heat entering the alarm. Keep at least 300 mm away from walls. Wall Mounting Do not mount tight into the corners- Put the top edge of your smoke alarm between 150 and 300 mm below the ceiling. Keep at least 300 mm from room corners. On a Sloping Ceiling In areas with sloping or peaked ceilings install your Smoke Alarm goo mm from the highest point measured horizontally because “dead air” at the apex may prevent smoke from reaching the unit. Areas to be avoided include the following Situations where the temperature may fall below OOC or rise above 400C. Humid areas such as bathrooms, kitchens, shower rooms where the relative humidity may exceed 90%. Near a decorative object, door, light fitting, window molding etc., that may prevent smoke or heat from entering the alarm. Adjacent to or directly above hot compo- nents such as radiators or wall vents that can effect the direction of air currents. In very dusty or dirty environments such as workshops. Locate unit at least 1.5 m and route wiring at least 1 m away for fluorescent light fit- tings as electrical “noise” and/or flickering may affect the unit Do not wire into the same circuit as fluorescent lights or dim- mers. Do not locate in insect infested areas. Insects and contamination on the Heat Alarm sensor can increase its response time. HUSH OR SILENCE FEATURE This Srnoke Alarm has a built-in Hush or Silence feature incorporated into the Test button. If cooking or other non-hazardous sources cause the unwanted alarm, it can be tem- porarily silenced by depressing the test button and holding for approximately 3 seconds. The alarm will enter a dormant period for up to 15 minutes. The red LED will flash every 10 seconds to indicate the sensitivity is reduced. At the end of the hush period the alarm will then reset to normal sensitivity. NOTE – If the smoke density increases du- ring this period (i.e. from a fire) the unit will go into alarm mode. MAINTAINING YOUR SMOKE ALARM If the smoke detector emits a short ‘beep’ approximately once a minute the battery is at the end of its life and should be replaced immediately. This low voltage warning will be given for at least 7 days. A fresh battery should last for approximately one year. If the red indicator light (LED) does not flash every minute then replace the bat- tery. Test the alarm for correct operation using test facility, whenever the battery is repla- Clean your smoke alarm regularly to pre- vent dust build up. This can be done using a vacuum cleaner with the brush attach ment- Clean gently around the front grilled section and sides. The apparatus shall not be exposed to dripping or splashing. IMPORTANT SAFEGUARDS Installation of your smoke alarm is only one step in your safety plam Other im- portant steps should be taken to further improve your safety. Install the smoke alarm properly, following this instruction leaflet. Test your smoke alarm weekly Replace the battery immediately once depleted. Do not smoke in bed. Keep matches & lighters away from children. Store flammable materials in a proper manner and never use them near naked flames or sparks. Maintain emergency equipment such as Fire Extinguishers, escape ladders etc and ensure all occupants know how to use them correctly. Plan an escape route/s from your building in advance and ensure all occupants are aware of them. Re-enforce this awareness periodically through-out the year. Make sure escape routes remain free of any obstructions. THIS PRODUCT IS A SEALED UNIT AND CANNOT BE REPAIRED – IF THE UNIT IS TAMPERED WITH IT WILL INVALI- DATE THE GUARANTEE IF THE UNIT IS FAULTY PLEASE RETURN ITTO YOUR ORIGINAL SUPPLIER WITH YOUR PROOF OF PURCHASE. YOUR SMOKE ALARM GUARANTEE These Smoke Alarms are guaranteed to be free from defects in materials and work- manships under normal use and service for a period of five years from date of pur- chase. The company will not be obligated to repair or replace parts which are found to be in need of repair because of misuse, damage or alterations occur after the date of purchase. Send the Smoke Alarm with proof of purchase, postage and return postage prepaid, to local distributor. The liability of the company arising from the sale of this Smoke Alarm shall not in any case exceed the cost of replacement of Smoke Alarm and in no case shall the company be liable for consequential loss or damages resulting from the failure of the Smoke Alarm CORDES VERTRIEBSGESELLSCHAFT MBH SHALL HAVE NO LIABILITY FOR ANY PERSONAL INJURY OR PRO- PERTY DAMAGE, OR ANY SPECIAL INCIDENTAL, CONTINGENT OR CON- SEQUENTIAL DAMAGE OF ANY KIND RESULTING FROM A FIRE. THE EX- CLUSIVE REMEDY FOR BREACH OF THE LIMITED WARRANTY CONTAINED HEREIN IS THE REPAIR OR REPLACE- MENT OF THE DETECTIVE PRODUCT AT CORDES VERTRIEBSGESELL- SCHAFT MBH OPTION. IN NO CASE SHALL CORDES VERTRIEBSGESELL- SCHAFT MBH’S LIABILITY UNDER ANY OTHER REMEDY PRESCRIBED BY LAW EXCEED THE PURCHASE PRICE. YOUR SMOKE ALARMS IS NOT A SUBSTITUTE FOR PROPERTY, DISABILITY, LIFE OR OTHER INSURANCE OF ANY KIND. AP- PROPRIATE COVERAGE IS YOUR RE- SPONSIBILITY. CONSULT YOUR INSURANCE AGENT This does not affect your statutory rights. This alarm is only suitable for single occu- pancy private dwellings only and not inten ded for multi occupancy private dwellings or commercial or industrial dwellings.
FREE ENGLISH PDF
USER GUIDE – USER MANUAL
OWNER GUIDE – OWNER MANUAL
REFERENCE GUIDE – REFERENCE MANUAL
INSTRUCTION GUIDE – INSTRUCTION MANUAL